Condensate Blow off on ARUF, ARPT and AVPTC Air Handlers
Type: Service Alert
Equipment: Air Handler
Recall or Alert Date: 06-03-2014
Serial Number: SR-060
Brands Affected: AmanaGoodman
We have received some reports of condensate blow off on ARUF/PT and AVPTC Smart Frame™ air handlers when installed in the horizontal left position. The majority of the reports involve the “D” chassis air handlers.
Testing has determined that air leaks around the triangle endplates and coil top plate caused condensate blow off and to resolve this issue redesigned triangle endplates and insulation on the top plate of evaporator coil has been added in production beginning serial date code of 1405.Affected Products: